Program the Flexput circuit as a notification circuit, Refer to Section 9.5.3. Assign this Flexput to an output
group that is mapped to activate with non silenceable constant output in response to a system general alarm
condition. It is not possible to reset the remote indication until you clear the condition and reset the control
All circuits off the 5220 are
non- power limited and
all wiring is non-supervised.
The wiring off the main control
is still power limited and supervised.
Using the Addressable Relay Module for City Box
Wire the Relay module as shown in Figure 4-58.
in City Box
NFPA 72 Polarity Reversal
Note: Intended for connection to a polarity reversal circuit of a control unit at the protected premises having
Figure 4-57 City Box Connection
Figure 4-58 Relay Module for City Box Connection
Control Panel Installation
Not suitable for remote
premise service where
circuits are required for
fire supervisory (if
applicable), and trouble
Note: Flexput circuit
1 used as an example.
Any Flexput circuit
could be used