The Energy Pack can be mounted on a standard EN50022
DIN rail or an equipment panel. It is designed to be
mounted adjacent to the Controller and connected to the
Controller using the provided cable (IC695CBL003).
Heat dissipation: When mounting the Energy Pack,
allow a minimum clearance of 25.4mm (1 inch) on all four
sides of the unit (right, left, top and the bottom).
Mounting the Energy Pack on a DIN Rail
The Energy Pack snaps easily onto the DIN rail. No tools
Incline Energy Pack so that top edge of plastic
recess (Figure 2) engages top of DIN rail
Swivel the Energy Pack so that bottom spring-
loaded plastic clip engages bottom of DIN rail.
Listen for click as plastic clip springs back,
securing the Energy Pack onto the DIN rail.
IC695ACC403 Quick Start Guide
Energy Pack. Includes base,
CapPack module and Energy Pack
to Controller cable.
Replacement CapPack module.
Replacement 0.6m (24") Energy
Pack to Controller cable.