SANYO AIR CONDITIONING PRODUCTS
DUCTLESS SPLIT SYSTEM AIR CONDITIONERS
SPECIFICATIONS - SECTION 15700
Covers Sanyo System Models > 09KS51, 09KLS51, 12KS51, 12KLS51, 18KS52, 18KLS52,
(See plans for specified model(s) & details)
DUCTLESS SPLIT SYSTEM AIR CONDITIONERS - WALL MOUNT TYPE
1) GENERAL SPECIFICATIONS
Furnish & install a Sanyo manufactured Ductless, Split System Air Conditioner(s), consisting of
an indoor, high wall mounted evaporator/blower section & matching outdoor condensing section.
System(s) shall bear the ARI label showing that the system(s) is ARI 210 or 240 & 270 Certified.
Systems shall be listed by CSA International and bear the C-CSA US label. Matching systems
shall meet or exceed the minimum, Federally mandated Seasonal Energy Efficiency Rating
(SEER) of 10 as certified by the ARI testing programs. System(s) indoor & outdoor units will
operate at sound levels equal to or below specified system(s) (see plans). Installation & Owners
Manuals shall be provided with each system.
Matching indoor & outdoor sections shall be connected by deoxidized, annealed refrigerant copper
tubing, type "L", cleaned & capped. All systems shall have flared refrigeration connections on
both indoor & outdoor sections. Size & insulate tubing according to manufacturer's specifications.
System(s) indoor & outdoor sections shall be completely factory assembled & wired, with a pre-
charge of refrigerant. A single power source shall provide voltage to both the outdoor & indoor
units. Electrical wire & connections to outdoor section, and between indoor & outdoor section(s),
shall be sized, installed & grounded by the installer in conformance with the National Electrical
Code (N.E.C.), local codes, as well as, manufacturer's instructions.
System(s) shall be equipped with a microprocessor control system, utilizing an infrared remote
controller with LCD display that provides access to all system functions, and transmits programs
to the indoor microprocessor every 5 minutes. Infrared remote controller shall be capable of
operating system mounted up to 26' from the indoor section, according to manufacturer's
recommendations & instructions. System(s) shall have the capability of continuous operation in
the case of a lost or damaged remote controller, utilizing a factory installed, integral manual
switch in conjunction with the system microprocessor.
System Infrared Remote Controller Functions will include: system mode selection,
programmable temperature control, 24hour programmable timer, one (1) hour off timer,
automatic three (3) speed indoor fan speed control, constant fan speed selection, night setback
mode, automatic sweep/flap control, multiple system control using a single controller.
1B) System Features will include: Sanyo high efficiency, rotary compressor, cap tube refrigerant
control, indoor coil freeze protection, built-in auto restart after power failure, short cycle time