KPI UNITS INSTALLATION
3.1 UNIT INSTALLATION
Check to ensure that the following accessories are packed with
N O T E
Install the KPI unit with a proper clearance around it paying
careful attention of installation direction for the piping, wiring and
maintenance working space, as shown below.
Install the unit with a proper clearance around it for operation
Consider the air distribution from the unit to the space of
the room, and select a suitable location so that uniform air
temperature in the room can be obtained.
Avoid obstacles which may hamper the air intake or the air
Select a position for introducing the outside air where no
where it will not be covered by snow.
PMML0371A rev.1 - 08/2016
Rubber duct joint
1 Preparing the sling Bolts.
2 Hanging the Unit.
3 Remove the screws at the top mounting position.
4 Remove the suspension bracket and attach them at higher
5 Tighten up the screws in the screw hole where the
Hang the suspension bracket on the anchor bolts and
Tighten up securely using double nuts in order to prevent
C A U T I O N
N O T E
suspension brackets were removed in order to prevent air