10 PROFIBUS GATEWAY MODULE (PGM) CONFIGURATION EXAMPLE
Double-click the master (PROFIBUS Gateway) in the Network view.
The configuration window appears. The Device Assignment menu in the Navigation Area is selected by
Click the Process Data menu in the Navigation Area.
The process data of the ET 200M(IM153-1) device appear in the right pane.
Select the Input_1 tag in the Tag column and modify it as Input_1_Exm.
Select the Output_1 tag in the Tag column and modify it as Output_1_Exm.
Drag-and-drop the GENDSB from the DSB library to the PBLINK_2230.
The Load Dialog box appears.
Double-click the GENDSB.
Type the name of the DSB (a maximum of 16 characters) or accept the default.
Click the PDC tab.
Select the Digital inputs ch 0-31 and Digital outputs ch 0-31 from the PDC Type list.
Type the description for the Digital inputs ch 0-31 PDC as "Digital input channel" in the PDC Description
Type the description for the Digital output ch 0-31 PDC as "Digital output channel" in the PDC Description
Select the tag Input_1_Exm for the input PDC and Output_1_Exm for the output PDC type in the Net Tag
Name column respectively.
When you select the Digital inputs ch 0-31 or the Digital output ch 0-31 row, the lower grid will display 4
rows (one row for each column) with all the channel information.
Enter 4 in the Number of Channels column for both the input and output types.
Drag-and-drop the PIOMB block from the PGM_IF library to the CEE of the C300 Controller.
Double-click the PIOMB (PIOMB_2239).
Click the point picker
The Point Selection dialog box appears.
Choose the PDC with the PDC description as "Digital input channel" to be associated to the PIOMB.
Repeat step 34 through step 37 to associate a PDC with the PDC description "Digital output channel" to
The PDC Name Reference field will display the PDC name that is associated to the PIOMB in the Main tab
of the PIOMB block.
Drag-and-drop the PBDICHANNEL from the PGM_IF library in to the Control Module containing the
on the Field Network Configuration tab toolbar.
When you click Save
, the configuration is saved temporarily.
to view the input and output modules that are assigned to the ET 200M(IM153-1) device.
button next to the PDC Name Reference box.