Profibus PA slave fault alarm
Module fault in PA network
Profibus PA Gateway fault
Profibus PA slave fault
Diagnostic data is corrupted
Data status below limit in PDC <PDC number>
This alarm is reported by the GENPADSB if any of the following
diagnostics is active:
This alarm is reported by the GENPAGWDSB if any of the module/
slot referred by the PDC configuration has diagnostic data, is failed, or
has status that is not "Module OK".
This is alarm is reported by the GENPAGWDSB if the gateway status
indicates "Configuration fail" or "Invalid bus parameter."
This alarm is reported by the GENPAGWDSB if any of the slaves in
the PA network report slave or channel-based diagnostics.
This alarm is reported by the GENPAGWDSB if the structure of the
IM-157 diagnostic data is corrupted.
This alarm is reported by the GENPADSB and/or the GENPAGWDSB
whenever the channel status is below the defined first acceptable PA
For this alarm to be reported, you must define the first acceptable PA
status value while configuring the GENPADSB and/or
7 DEVICE SUPPORT BLOCK (DSB)