Neural radio fire
Radio manual call
Optical-thermal fire detector with radio
transmission to the radio gateway
Indirect activation via radio gateway
SWING manual call point, activation via
radio gateway FDCW241
VESDA LaserFocus (laser monitoring)
Table 1: Devices which can be connected to the C-NET detector line
Possible / available
Not possible / not available
Availability is communicated with the delivery release
Check with your country representative that this detector is approved for
C-NET in your country.
Most devices are supplied via the detector line.
The input/output module FDCIO223 must have an external power supply.
All ↑ C-NET devices have an integrated line separator.
Influencing the earth fault monitoring
For devices on the C-NET with a separate supply, the supply must be
electrically isolated. FDCIO223 is an exception to this rule.
The number of connectable devices depends on the specific AK, RK, MK
connection factor of the type and is calculated using the 'Quantities Tool' software.
Note the specifications of the individual C-NET devices in the 'List of Compatibility'
document, see 'Applicable documents' chapter.
1 C-NET detector line [➙ 31]
Connectable C-NET devices
35 | 62