4.1 Mounting instructions
16 | 62
The station's equipment pack contains an mounting model with the dimensions
needed and details of the mounting points to assist with mounting.
The station must be assembled in a dry, clean and well vented room.
The station must be assembled at a distance of least one door leaf width from the
room's entrance. Select the height of mounting such that the display and optical
indications are approx. 1.6 -1.7m above where the observer stands.
The station and its components should be protected from dampness and interfering
external influences such as dust, great temperature fluctuations and mechanical
The station must be assembled in a place freely accessible to authorized staff and
the emergency services.
A level, non-vibrating wall surface with load bearing capacity and suitable mounting
materials (e.g. screws and plugs) are needed to secure the station to the wall.
The mounting surface and selected mounting must be suitable for the weight of the
equipped station incl. the batteries used.
The station may only be fitted using the 19" method if using the associated
Mounting is not permitted in rooms with high levels of electromagnetic interference,
e.g. in control rooms or right next to power cables and inductive loads.
Mounting and installation work may only be undertaken by qualified staff and
when the system is de-energized.
Damage resulting from electrostatics
Take appropriate EMC protective measures when handling electronics modules.