USB memory mode
Project data file number
(displays 1 to 99,
unrelated to the number
of files saved in the USB
• The following data can be copied by copying the project data via USB memory device.
• If the project data of the PLC function is locked with a password using FR Configurator2, copying to the USB memory device
and verification are disabled. Also if set to write-disabled, writing to the inverter is disabled. (For the details of the PLC function,
refer to the PLC Function Programming Manual and the Instruction Manual of FR Configurator2.)
Parameters referred to
Pr.338 Communication operation command
5.11.17 Trace function
• The operating status of the inverter can be traced and saved on a USB memory device.
• Saved data can be monitored by FR Configurator2, and the status of the inverter can be analyzed.
Parameter setting mode
Function block source information
Global text comment information
Project management information
Fault history mode
Overwrite the inverter project data file onto the designated
file in the USB memory device.
Write the designated project data file of the USB memory
device onto a data file of the inverter.
Verify the designated project data file of the USB memory
device against the project data file of the inverter.
Copy from inverter to USB
Copy from USB memory
device to inverter
5.11 (A) Application parameters