GOT-F900 SERIES (CONNECTION)
Setting of Connected Equipment for GOT
The setting in the screen creation software is required to turn on and off the function keys and LED
display using the connected equipment. This section describes the setting method.
1) GOT-F900 Series
No setting is enabled on the GOT. Set items in either one of the screen creation software mentioned
2) GT Designer2
Installation and Wiring of F920GOT-K/F930GOT(-K)/F940(W)GOT 4
a)It is supposed that the GT Designer2 has started up and the
screen data to be set is read.
b)Open a user screen to be set.
Any screen is available as far as it has been already created.
Select and display the base screen (B-1) in this example.
c)Select "Object"-"Lamp"-"External" on the menu.
d)Click the [Dev..] button, input a bit device to be assigned, then
Refer to Caution on setting of "Lamp (External)" described later.
e)To a function key, a same function can be set in the entire project,
or a different function can be set for each screen. The required
procedure is as described below.
Unit of project (common on all screens)
From the menu bar, select "Common"-"Operation Panel".
Or double-click "Operation Panel" in the tree displayed in the
project work space.
Display (screen name)
The "Lamp" dialog box
"Operation Panel" dialog