Rated supply voltage U*
Recommended rated current of the protective
Contactor relay (69.)
*) The operator's supply voltage may deviate from the rated supply voltage of the
vacuum circuit-breaker module by -15 % to +10 %.
**) Built-in automatic circuit-breaker with C characteristic
Recommendation for motor protection device
Contactor relay K1
After the supply voltage is applied and if the closing
spring is discharged, the motor starts immediately and
is automatically deactivated internally after charging has
Power consumption, maximum:
in the event of direct voltage approx. 750 W
in the event of alternating voltage 1400 W.
In the short charging time, the motor temporarily oper-
ates in the overload range. See Fig. 12 for the rated cur-
rent for the required motor short-circuit protection.
Note: The motor protection devices are not included in
the delivery of the vacuum circuit-breaker module and
must be ordered separately.
If simultaneous CLOSED and OPEN commands are
continuously applied to the vacuum circuit-breaker, it
returns to the open position after being closed.
Via the function of the contactor relay K1, the vacuum
circuit-breaker pauses there until the CLOSE command
is given again.
This prevents continuous closing and opening (pump-
AC 50/60 Hz
AC 50/60 Hz
9229 9923 176 0B