Decommissioning the machine
Damage as a result of an extended period out of service
If the machine is going to be out of service for longer than six months, then take the necessary
measures for preservation and storing. Otherwise damage to the machine will result.
Record the decommissioning steps. This log will be useful upon recommissioning.
Re-commissioning the machine
When you re-commission the machine, proceed as follows:
● Study the record made when the machine was decommissioned, and reverse the measures
● Perform the measures listed in the "Commissioning" section.
Start-up (Page 83)
Inspections in the event of faults
Natural disasters or unusual operating conditions, such as overloading or short circuit, are
faults that overload the machine electrically or mechanically.
Immediately perform an inspection after such faults.
Correct the cause of the fault as described in the respective remedial measures section. Repair
any damage to the machine.
that were taken for conservation and storage.
SIMOTICS TN Series N-compact 1LA8
Operating Instructions 05/2014