1.3 ENERVISTA UR SETUP SOFTWARE
Select "Ethernet" from the Interface drop-down list. This will display a number of interface parameters that must be
entered for proper Ethernet functionality.
Enter the relay IP address specified in the
) in the "IP Address" field.
10. Enter the relay slave address and Modbus port address values from the respective settings in the
11. Click the Read Order Code button to connect to the B30 device and upload the order code. If an communications
error occurs, ensure that the three EnerVista UR Setup values entered in the previous steps correspond to the relay
12. Click OK when the relay order code has been received. The new device will be added to the Site List window (or
Online window) located in the top left corner of the main EnerVista UR Setup window.
The Site Device has now been configured for Ethernet communications. Proceed to the Connecting to the B30 section to
a) USING QUICK CONNECT VIA THE FRONT PANEL RS232 PORT
Before starting, verify that the serial cable is properly connected from the laptop computer to the front panel RS232 port
with a straight-through 9-pin to 9-pin RS232 cable.
Verify that the latest version of the EnerVista UR Setup software is installed (available from the GE EnerVista CD or
online from http://www.gegridsolutions.com/multilin). See the Software Installation section for installation details.
Select the "UR" device from the EnerVista Launchpad to start EnerVista UR Setup.
Figure 1–5: CONFIGURING ETHERNET COMMUNICATIONS
B30 Bus Differential System
1.3.4 USING THE QUICK CONNECT FEATURE
1 GETTING STARTED