Water Trap Replacement
The water trap is intended to protect the
AGENT system from humidity, secretions,
bacterial contamination and dust. Replacement
of the water trap is necessary when the
contents in the water trap reach its full line.
Always discard the water trap when it becomes filled. Do not attempt to clean or reuse the water
trap. Accidental water ingress into the system can affect the gas measurements.
To replace the water trap
Expression MR400 Instructions for Use
The water trap must be checked every 17 hours of use and replaced as necessary. (Dispose
of the trap according to your facility's biohazard procedure.)
For optimum fit and compatibility, use only Invivo (Royal Philips) specified parts.
If a sampling line is connected, then remove the sampling line from the
sample port on the water trap.
While simultaneously pressing both release tabs on the water trap,
remove the water trap from the water trap receptacle then dispose of
the water trap properly.
Water trap receptacle
Monitoring Agents and Gases (AGENT Option) 9‐13