1 GETTING STARTED
1 GETTING STARTED 1.1IMPORTANT PROCEDURES
Please read this chapter to help guide you through the initial setup of your new GE Mutilin structured template.
Before attempting to install or use the device, review all safety indicators in this document to help prevent injury,
equipment damage, or downtime.
The following safety and equipment symbols are used in this document.
Indicates a hazardous situation which, if not avoided, will result in death or serious injury.
Indicates a hazardous situation which, if not avoided, could result in death or serious injury.
Indicates a hazardous situation which, if not avoided, could result in minor or moderate injury.
Indicates practices not related to personal injury.
Open the relay packaging and inspect the unit for physical damage.
View the rear nameplate and verify that the correct model has been ordered.
Line Differential Relay
Tel: (905) 294-6222
Fax: (905) 201-2098
Ensure that the following items are included:
• Instruction manual.
• GE EnerVista CD (includes the EnerVista UR Setup software and manuals in PDF format).
• Mounting screws.
For product information, instruction manual updates, and the latest software updates, please visit the GE Digital Energy
website at http://www.gedigitalenergy.com.
If there is any noticeable physical damage, or any of the contents listed are missing, please contact GE Digital
GE DIGITAL ENERGY CONTACT INFORMATION AND CALL CENTER FOR PRODUCT SUPPORT:
GE Digital Energy
215 Anderson Avenue
Canada L6E 1B3
Figure 1–1: REAR NAMEPLATE (EXAMPLE)
1-800-547-8629 (North America only)
L90 Line Current Differential System
1.1 IMPORTANT PROCEDURES
1.1.1 CAUTIONS AND WARNINGS
88-300V DC @ 35W / 77-265V AC @ 35VA
300V DC Max 10mA
Standard Pilot Duty / 250V AC 7.5A
360V A Resistive / 125V DC Break
4A @ L/R = 40mS / 300W
1.1.2 INSPECTION CHECKLIST