GSMV4G/GSMVCN4G Installation and Setup Guide
8. Replace lower printed circuit board and then daughter card, as shown in Step D above.
Be sure to engage receptacle pins by pushing in before securing the daughter card with
When all wiring is completed, attach the case front. Position the top first, then press the
bottom section until it snaps in place. Secure bottom using the supplied cover screw.
Wiring the Communicator
Installation must be in accordance with the National Electrical code and UL681, Installation and
Classification for Burglar and Hold-Up Alarm Systems.
The communicator must be connected to a UL Listed dry contact or voltage trigger outputs of a UL
Listed compatible control panel.
All interconnecting wires between the UL Listed control panel and the communicator must be less
than 3 feet in length contained in the same room. All interconnecting wiring must be installed in rigid
or EMT (where exposed on interior walls) or in flexible metal tubing if run in the walls or ceiling.
Requires dialer reporting with a UL Listed control panel. Reporting occurs over both paths.
A UL listed control panel must monitor the radio fault output of the communicator. A No. 659 or other
UL listed Telco Line Fault Monitor's output must be connected to an input zone on the communicator.
Premises openings and closings should be sent via the UL listed control panel.
For ULC Commercial Fire and Burglary installations, only use the ULC wiring specified in the "Power
Connections and Options" topic.
Wiring for two-way voice
The GSMV4G requires an optional audio cable (GSMV-AUDIO, grey) to support two-way
voice using the AVS Base Unit. Note the AVS Base Unit is part of Honeywell's AVS Audio
Verification System. This system consist of the AVS Base Unit, Remote Station, and the
Remote Station PC board. For detailed information, refer to the AVS Audio Verification
System documentation. Follow the guidelines below for connecting the audio cable.
1. Power down the communicator, control panel and AVS Audio Verification System.
(When the communicator is fully wired up, restore power to the communicator, control
panel and AVS Audio Verification System.)