INSTALLATION AND WIRING
Install a programmable controller according to the installation environment shown in the general specifications. (Page 84
Do not install the programmable controller to the following place.
• Ambient temperature is outside the range of 0 to 55
• Ambient humidity is outside the range of 5 to 95%RH.
• Condensation occurs because of rapid temperature change.
• Corrosive gas or combustible gas exists.
• Conductive powder such as dust and iron powder, oil mist, salinity, or organic solvent is filled.
• Programmable controller is exposed to direct sunlight.
• Strong electric field or strong magnetic field is generated.
• Programmable controller is subject to vibration and shock.
*1 When an extended temperature range base unit is used, each module can be used in the environment of 0 to 60.
5 INSTALLATION AND WIRING
5.1 Installation Environment