Level 3 Quick Commissioning
Parameters, designated with a * offer more setting possibilities than are actually listed here. Refer to
the parameter list on the supplied CD for additional setting possibilities.
Correct Motor information is very important – please refer to section 5.4 for detailed information. For
multi-motor (parallel motors) please see the operating instructions for further details.
Parameters with "" after the number are referring to index 0 of that parameter. For example, if you
read P0300=1 it means that you should set P0300 index 0 to a 1.
You can enter your own settings in the user settings column for quick reference
Set User Access Level *
Start Quick Commissioning *
P0010 must be set to 1 in order to parameterize the
Check/Set Frequency Setting (50/60Hz)
For P0100 = 0 or 1, the setting of switch DIP2(2) (under
I/O board) determines the value of P0100 (refer to the
If P0100 does not correctly reflect your motor data
(50/60Hz) at this point, please power down your
MICROMASTER and change the DIP2(2) switch
according to section 3 before continuing.
Failure to follow this procedure will result in
complete loss of your motor parameters at the next
Factory setting (refer to section 5.2)
USE DIP2(2) Switch - 50Hz, kW (typically
European IEC Motors)
USE DIP2(2) Switch - 60 Hz, HP (typically North
American NEMA frame motors)
60 Hz, kW (Typically found in Asian market)
Quick Start Guide
kW, 50 Hz
HP, 60 Hz