When the GOT is connected to the remote I/O station in the MELSECNET/H network system, only the master station can be
The access range other than the above is the same as the one for when the GOT is connected with a controller.
For details of the access range, refer to the following.
■1. Monitoring word devices by 32 bits
When word devices are monitored by 32 bits (two words), those with 32 bits of data remaining are monitored.
Devices with 16 bits (one-word) of data remaining are not monitored.
If an odd number is specified for the first monitor device number, the last device number of the specified controller will
not be displayed.
■2. Changing the set values of timers and counters of the QnACPU and displaying device
For only QnACPUs whose number in the DATE column on the rating plate is [9707B] or later, the set values of timers
(T) and counters (C) can be changed and device comments can be displayed.
■3. Monitoring local devices using multiple software
When monitoring local devices, do not monitor the devices of the same PLC CPU simultaneously using multiple
software (including GT Designer3 and GX Works2). Otherwise the local devices cannot be monitored properly.
Operations Common to the Monitor Screens
This section describes the operations that are common to the monitor screens.
3 - 14
3.3 Operations Common to the Monitor Screens
D11129 D11130 D11131 D11132 D11133 D11134
Unit of the monitor display
DATE 9707 B
Manufacture year and month
3.3.1 Displaying the monitor screen
3.3.2 Names of each section of monitor screen
3.3.3 Display format of the monitor screen ([One large screen], [4 screens])
3.3.5 Entering devices ([Register])
3.3.6 Deleting a device ([Delete])
3.3.7 Deleting devices at a time ([Delete all])
3.3.8 Test operation for the monitor device ([Test])
3.3.9 Switching the display (number or columns, comment display) ([Layout])
3.3.10 Monitoring local devices ([Local monitor])
3.3.11 File switching for comment display ([Change comment])
3.3.12 Screen transition (common operation)
Nothing is displayed.