Defining Target Setting
Define the IP address or host name of STARDOM for
which the communication settings are made.
Double-click [Physical hardware]
and input the IP address or the host name.
Downloading the project
(1) Execute [Build] - [Make].
(Same as when pressing the function key F9).
(2) Download after confirming that the compile error
does not occur. Select [Download] in the project
control dialog displayed when [Online] - [Project
control] is selected.
(3) When the download is completed, select [Cold]
and start STARDOM.
When performing monitoring with the GOT connected
to a YOKOGAWA PLC and setting devices for objects,
use devices within the device range of the
When a device outside the range is set on an object, an
indefinite value is displayed on the object.
(No error is displayed in the system alarm.)
For details on the device range of YOKOGAWA PLCs,
refer to the following manual:
7.4 Device Range that Can Be Set
Connecting to STARDOM
(1) Redundant system
When STARDOM is configured with a redundant
system, the connection is not supported.
(2) System alarm
The PLC error does not appear in the system alarm.
(3) GOT clock control
Since the STARDOM does not have a clock function,
the settings of [time adjusting] or [time broad cast] by
GOT clock control will be disabled.
7. CONNECTION TO YOKOGAWA PLC
7.2 Serial Connection
7 - 15