CHAPTER 4: INTERFACES
CURRENT — Not used
FREQUENCY — Not used
OTHER — Indicates a digital element was involved
PHASE A — Not used
PHASE B — Not used
PHASE C — Not used
NEUTRAL/GROUND — Not used
The second and third panels provide 48 amber LED indicators whose operation is controlled by the user. Support for
applying a customized label beside every LED is provided.
User customization of LED operation is of maximum benefit in installations where languages other than English are used
to communicate with operators. See the User-programmable LEDs section in chapter 5 for the settings used to program
the operation of the LEDs on these panels.
Default labels for LED panel 2
The default labels are intended to represent the following:
GROUP 1...6 — The illuminated GROUP is the active settings group
Firmware revisions 2.9x and earlier support eight user setting groups; revisions 3.0x and higher support six setting
groups. For convenience of users using earlier firmware revisions, the relay panel shows eight setting groups. Even
though the LEDs have default labels, they are fully user-programmable.
The relay is shipped with the default label for the LED panel 2. The LEDs, however, are not pre-programmed. To match the
pre-printed label, the LED settings must be entered as shown in the User-programmable LEDs section of chapter 5. The
LEDs are fully user-programmable. The default labels can be replaced by user-printed labels for both panels as explained in
the next section.
4.2.8 Custom LED labeling
188.8.131.52 Enhanced faceplate
The following procedure requires these pre-requisites:
EnerVista UR Setup software is installed and operational
The C30 settings have been saved to a settings file
The UR front panel label cutout sheet (GE part number 1006-0047) has been downloaded from
C30 CONTROLLER SYSTEM – INSTRUCTION MANUAL
Figure 4-25: LED panels 2 and 3 (index template)
FRONT PANEL INTERFACE