[ IX Troubleshooting ]
4. Maintenance setting 1
This category includes items that are set during test run and maintenance.
Set the dip switches
SW2 and SW3.
Select the desired
item with the push
Press the push
switches SWP1 (↑) or
SWP2 (↓) to increase
or decrease the value.
Press the push switch
SWP3 to save the
Set the dip switches on the circuit board as follows.
By setting SW3-9 to ON after setting the dip switches SW2 and SW3 as shown left,
the setting values can be checked.
(The settings cannot be changed.)
Press the push switch SWP3 to toggle through the item codes listed below.
Press the push switches SWP2 and SWP3 to change the value of the selected item.
Refer to "Maintenance item (1) list" on the next page for information about the items that
can be set.
Press SWP3 once within one minute of changing the setting with SWP1 or SWP2 to
save the setting.
Once the new setting is saved, the display will stop blinking and stay lit. The display will,
then, return to the item code display mode.
If SWP3 is not pressed within one minute, the change will not be saved, and the display
will return to the item code display mode.
- 111 -