# Mitsubishi Electric FR-F700PJ Instruction Manual Page 264

Air-conditioning inverter.

<Set point input calibration>
1) Setting with terminal 2 input
1. Apply the input voltage of 0% set point setting (e.g. 0V) across terminals 2-5.
2. Enter in C2 (Pr. 902) the frequency which should be output by the inverter at the deviation of 0% (e.g. 0Hz).
3. In C3 (Pr. 902), set the voltage value at 0%.
4. Apply the voltage of 100% set point (e.g. 5V) across terminals 2-5.
5. Enter in Pr. 125 the frequency which should be output by the inverter at the deviation of 100% (e.g. 60Hz).
6. In C4 (Pr. 903), set the voltage value at 100%.
2) Setting with Pr. 133
When both or one of C42 (Pr. 934) and C44 (Pr. 935) is "9999".
For the set point, set a % converted value in the range of 0 to 100%.
When both of C42 (Pr. 934) and C44 (Pr. 935)  "9999".
For the set point, set PID coefficient, which corresponds with 0 to 100%.
<Measured value calibration>
1)When both or one of C42 (Pr. 934) and C44 (Pr. 935) is "9999"
1. Apply the input current of 0% measured value (e.g. 4mA) across terminals 4-5.
2. Make calibration using C6 (Pr. 904).
3. Apply the input current of 100% measured value (e.g. 20mA) across terminals 4-5.
4. Make calibration using C7 (Pr. 905).
2) When both of C42 (Pr. 934) and C44 (Pr. 935)  "9999"
1. Apply the input current of 0% measured value (e.g. 4mA) across terminals 4 and 5.
2. Set PID display value at 0% measured value (example: 15(C)) to C42 (Pr. 934) , and calibrate C43 (Pr. 934).
3. Apply the input current of 100% measured value (e.g. 20mA) across terminals 4 and 5.
4. Set PID display value at 100% measured value (example: 35(C)) to C44 (Pr. 935), and calibrate C45 (Pr. 935).
REMARKS
 The frequency set in C5 (Pr. 904) and Pr. 126 should be the same as set in C2 (Pr. 902) and Pr. 125 .
The results of the above calibration are as shown below:
Pr. 934,
Pr. 133
Pr. 935
Setting
Setting
Set point
9999
Set point
Both or one
is 9999
Other than
9999
Set point
Other than
9999
corresponding with 0 to 100%.
Set Point Setting
(Terminal 2)
(%)
100
Measured
Value
0
0
5 (V)
Set point signal input
(Pr.133)
(%)
100
0
C5(Pr.904)
Pr.126
Set point setting
(Pr.133)
Measured
value
(%)
100
0
C42(Pr.934)
C44(Pr.935)
Set PID coefficient
Special operation and frequency control
Measured Value
Manipulated Variable
(Terminal 4)
(%)
100
0
0
4
20
(mA)
Manipulated
C6(Pr.904)
C7(Pr.905)
Variable(Hz)
Measured value
input signal
C2(Pr.902)
(%)
100
0
0
4
20
(mA)
C43(Pr.934)
C45(Pr.935)
Measured value
input signal
60
(Pr.125)
0
0
100
Deviation(%)
4
259