Base frequency voltage setting (Pr. 19)
Use Pr. 19 Base frequency voltage to set the base voltage (e.g. rated motor voltage).
If the setting is less than the power supply voltage, the maximum output voltage of the inverter is as set in Pr. 19.
Pr. 19 can be utilized in the following cases.
(a) When regeneration is high (e.g. continuous regeneration)
During regeneration, the output voltage becomes higher than the reference and may cause an overcurrent trip
(E.OC) due to an increased motor current.
(b) When power supply voltage variation is large
When the power supply voltage exceeds the rated voltage of the motor, speed variation or motor overheat may be
caused by excessive torque or increased motor current.
Changing the terminal assignment using Pr. 178 to Pr. 182 (input terminal function selection) may affect the other
functions. Set parameters after confirming the function of each terminal.
Parameters referred to
Pr. 14 Load pattern selection
Pr. 29 Acceleration/deceleration pattern selection
Pr. 83 Rated motor voltage, Pr. 84 Rated motor frequency
Pr. 178 to Pr. 182 (input terminal function selection)
General-purpose magnetic flux vector control
Refer to page 105
Refer to page 118
Refer to page 125
Refer to page 134
Refer to page 93