Read the Safety Instruction sheet before installing the UPS. Unpacking Inspect the UPS upon receipt. APC designed robust packaging for your product. However, accidents and damage may occur during shipment. Notify the carrier and dealer if there is damage. The packaging is recyclable; save it for reuse or dispose of it properly.
Positioning the UPS Place the UPS where it will be used. The UPS is heavy. Select a location sturdy enough to handle the weight. Do not operate the UPS where there is excessive dust or the temperature and humidity are outside the specified limits.
Installing and Connecting the Battery and Attaching the Front Bezel Step 1 Step 3 Connect battery plug to UPS. Tuck white battery cord into space above connector. Connecting Equipment and Power to the UPS -UPS R MART ANEL 100/120V Models 120V Model Only: Site wiring fault indicator 230V Models Step 2...
Serial Port USB Port Use an APC supplied cable to connect to the Serial Port. DO NOT use a stan- dard serial interface cable since it is incompatible with the UPS connector. Both Serial and USB Ports are provided. They cannot be used simultaneously.
2: O PERATION -UPS F MART RONT ANEL Power On Power Off Online AVR Trim AVR Boost On Battery Overload The online LED illuminates when the UPS is supplying utility power to the connected equipment. If the LED is not lit, the UPS is either not turned ON, or is supplying battery power.
UPS battery life differs based on usage and environment. It is recommended that the battery/batteries be changed once every three years. See the APC web site, www.apc.com, for on battery run times. Failure of a battery self-test causes the UPS to emit short beeps for one minute and the replace battery LED illuminates.
3: U ONFIGURABLE ETTINGS ARE MADE THROUGH SUPPLIED UNCTION Automatic Self-Test Every 14 days (336 hours) UPS ID UPS_IDEN Date of Last Battery Re- Manufacture placement Date Minimum Capacity Before 0 percent Return from Shutdown Voltage Sensitivity The UPS detects and reacts to line voltage distortions by transferring to battery operation to protect the...
ETTINGS ARE MADE THROUGH SUPPLIED UNCTION Low Battery Warning. PowerChute interface software provides auto- matic, unattended shut- down when approximately two minutes (by default) of battery operated run time remains. Synchronized Turn-on 0 seconds Delay High Transfer Point 100V: 108VAC 120V: 127VAC 230V:...
Refer to Installing and Connecting the Battery and Attaching the Front Bezel, in this manual. Refer to Mounting the UPS in a Rack (Steps 1 and 2) for instructions on battery removal. Be sure to deliver the spent battery to a recycling facility or ship it to APC in the replacement battery packing material.
5: T ROUBLESHOOTING Use the chart below to solve minor Smart-UPS installation and operation problems. Refer to the APC web site, www.apc.com, for assistance with complex UPS problems. ROBLEM AND OSSIBLE AUSE WILL NOT TURN ON Battery not connected prop- erly.
EMITS A SUSTAINED ALARM TONE The connected equipment exceeds the specified “maximum load” as de- fined in Specifications at the APC web site, www.apc.com. The alarm remains on until the overload is removed. Disconnect nonessen- tial equipment from the UPS to eliminate the overload.
Check that the UPS is properly installed allowing for adequate ventila- tion. Allow the UPS to cool down. Restart the UPS. If the problem continues contact APC at, www.apc.com/supoport. EATURE The UPS has a diagnostic feature that displays the utility voltage. Plug the UPS into the normal utility power.
If the UPS is under warranty, repairs are free. If not, there is a repair charge. 3. Pack the UPS in its original packaging. If the original packing is not available, refer to the APC web site, www.apc.com/support, for information about obtaining a new set.
6: R EGULATORY AND Regulatory Agency Approvals and Radio Frequency Warnings 230V MODELS This is a Class A product. In a domestic environment this product may cause radio interference, in which case the user may be required to take corrective actions. 120V MODELS This equipment has been tested and found to comply with the limits for a Class A digital device, pur-...
Limited Warranty American Power Conversion (APC) warrants its products to be free from defects in materials and workmanship for a period of two years from the date of purchase. Its obligation under this warranty is limited to repairing or replacing, at its own sole op- tion, any such defective products.