Plymouth, MN 55441-4437 This warranty does not cover removal or reinstallation coats. This warranty shall not apply if It is shown by Honeywell that the defect or malfunction was caused by damage which occurred while the product was in the possession of a consumer.
STEP 9 Mount The Thermostat ....................24 STEP 10 Check Thermostat Operation After Programming And installing ......25 STEP 11 Set The Fan And System Switches .
~ Prepare For Installation Check Table 1 to make sure this thermostat is compatible with your system. If it is not, return to retailer. For more information, call Honeywell Customer Assistance, toll-free 1-800-468-1502. TABLE 1 -COMPATIBILITY CHART. System Type Gas-Standin~ Pilot...
We recommend Energizer batteries. •l Make sure the thermostat is set in the OFF position. El Use a coin to remove battery door.
~ The temperatures cannot be set any higher than 88° F [31 NOTE: If you decide not to program the thermostat, it will automatically control heating at 68° F [20° C], and cooling at 78° F [26° C], 24 hours a day.
This guide can be used for programming your new thermostat. NOTE: Batteries are required for operation and programming. When inserting batteries, set system switch to OFF. Remove battery door (on thermostat left side) using a coin at the bottom. Follow instructions on pages 6 and 7.
A and B on the back of the thermostat. Use the heating system table shown in the illustration, (page 17) as a guide. The system on-time should be optimized according to the type of system to minimize room temperature swings.
NOTE: This thermostat does not have a setting for steam/gravity air. Cycles would not be long enough for accurate temperature control. IMPORTANT: When using a high efficiency furnace such as a 90 percent or greater Average Fuel Utilization Efficiency (AFUE) unit, adjust screw A OUT ONE TURN and screw B IN.
_ Mount The Thermostat A. ENGAGE TABS AT TOP OF THERMOSTAT AND MOUNTING PLATE. NOTE: To remove thermostat from wall, first pull out at bottom of thermostat, removing top last. *4 Check Thermostat Operation Programming And Installing HEATING Do not check heating system...
Exception: When Fan Operation Switch on back of thermostat is set to “E” position (see page 16), fan will operate with furnace only. FAN ON: The fan runs continuously.
If temperature setting is higher than current tempera- ture, and SYSTEM ON indicator is lit, contact Honeywell Customer Assistance at 1-800-468-1502. Check that switch on thermostat is set to COOL. Check the system fuse or circuit breaker and replace or reset if necessary.
Toll-free Customer Assistance For all questions concerning this thermostat, please read and follow the instructions. If additional assistance is needed, call Honeywell Customer Assistance toll-free at 1-800-468- 1502, Monday-Friday, 7:00 a.m. -5:30 p.m. Central time. Before you call, please have the following information available: thermostat model number and date code, kind of heating/cooling system (i.e., hot water, warm air, oil, gas, etc.), and...