Interrupted Electronic Oil Primary APPLICATION The R7184A,B,P,U Interrupted Electronic Oil Primary is a line voltage, safety rated, interrupted ignition oil primary control for residential oil fired burners used in boilers, forced air furnaces and water heaters. The R7184A,B,P,U used with a cad cell flame sensor, operates an oil burner and optional oil valve.
R7184A,B,P,U INTERRUPTED ELECTRONIC OIL PRIMARY Electrical Ratings: Inputs: Voltage: 102 to 132 Vac, 120 Vac nominal. Current: 100 mA plus burner motor, valve and ignitor loads. Frequency: 60 Hz. Outputs: Relay Contacts: Burner: 120 Vac, 10 full load amperes (FLA), 60 locked rotor amperes (LRA).
60 seconds. 5. Safety switch locks out approximately in safety switch timing indicated on label. Indicator light flashes at 1 Hz rate. Ignition and motor stop and oil valve closes. R7184A,B,P,U INTERRUPTED ELECTRONIC OIL PRIMARY THERMOSTAT JUMPER REMOTE ALARM CIRCUIT LEGEND: POWER SUPPLY.
R7184A,B,P,U INTERRUPTED ELECTRONIC OIL PRIMARY R7184 JUMPER LINE VOLTAGE THERMOSTAT OR AQUASTAT® CONTROL BURNER MOTOR INTERRUPTED IGNITOR INTERMITTENT REMOTE ALARM ALARM CELL CELL CIRCUIT JUNCTION LEGEND: SCREW TERMINAL 1/4 IN. QUICK CONNECT TERMINAL POWER SUPPLY. PROVIDE DISCONNECT MEANS AND OVERLOAD PROTECTION AS REQUIRED.
3. Make sure limit control is closed. 4. Check contacts between ignitor and the electrodes. 5. Check the oil pump pressure. R7184A,B,P,U INTERRUPTED ELECTRONIC OIL PRIMARY 3. On: cad cell is sensing flame. 4. Off: cad cell is not sensing flame. DELAY TIMES:...
Idle mode. 3. When flame or light is not present: a. R7184A,U (if valve-on delay is disabled) will apply power to the burner motor and ignitor. b. R7184B,P,U (if valve-on delay is enabled) will apply power to the burner motor and ignitor, enter/complete valve-on delay period and then apply power to the valve.
L1 of R7184.) IMPORTANT: First remove one thermostat lead. Condition: Burner starts, then locks out on safety with indicator light flashing at 1 Hz rate (1/2 second on, 1/2 second off). 1. Check that limit switches are closed and contacts are clean.
R7184A,B,P,U INTERRUPTED ELECTRONIC OIL PRIMARY Table 5. Troubleshooting Information (Continued). Procedure 7. Listen for spark after burner turns on (after a 2 second delay. 8. Check indicator light after flame is established, but before oil primary control locks out. 9. Check cad cell sighting for view of flame.