5/2 Day 5/1/1 Day Non-Programmable CONTROL COULD CAUSE PERSONAL INJURY AND/OR 1F86-0471 Non-Programmable PROPERTY DAMAGE. APPLICATIONS 1F86-0471 Thermostat THERMOSTAT APPLICATION GUIDE Description Gas or Oil Heat Electric Furnace Heat Pump (No Aux. or Emergency Heat) Heat Pump (with Aux. or Emergency Heat)
INSTALLATION Once fully down, snap the door back into position. To WARNING replace the batteries, set system to OFF, following the instructions above. Thermostat installation and all components of the Figure 1 – Battery door shown open control system shall conform to Class II circuits per the NEC code.
THERMOSTAT QUICK REFERENCE Figure 4 – Home Screen Display Home Screen Description Room Time Temperature Setting Day of Week Temperature Displays the power level of the 2 "AA" batteries: indicates good power level. indicates batteries at about Temperature Up/Down half power. “Change ”...
INSTALLER/CONFIGURATION MENU Press the Menu button for at least 5 seconds. The display will show item #1 in the table below. Press Menu to advance to the next menu item. Press to change a menu item. INSTALLER/CONFIGURATION MENU MENU PRESS DISPLAYED Press REF.
INSTALLER/CONFIGURATION MENU 4) Energy Management Recovery: (this step is skipped if 9) System Mode Configuration – This thermostat is configured to be non-programmable). configured for Heat and Cool with Auto changeover Energy Management Recovery (E) On enables the (SYSTEM switch with Cool Off Heat Auto) default. It can thermostat to start heating or cooling early to make the also be configured for Heat and Cool (Cool Off Heat), building temperature reach the program setpoint at the...
OPERATING YOUR THERMOSTAT IMPORTANT! Choose the Fan Setting (Auto or On) Manual Operation (Bypassing the Program) Programmable Thermostats Set the FAN Switch to Auto or On. Fan Auto is the most commonly selected setting and runs Press and the HOLD button and adjust the temperature wherever you like.
PROGRAMMING (For Programmable Model Only) Energy Saving Factory Pre-Program The 1F80-0471 thermostats are programmed with the energy saving settings shown in the table below for all days of the week. If this program suits your needs, simply set the thermostat clock and press the RUN button. The table below shows the factory set heating and cooling schedule for all days of the week.
TROUBLESHOOTING Reset Operation Note: When thermostat is reset, installer configuration menu settings and programming will reset to factory settings. If a voltage spike or static discharge blanks out the display or causes erratic thermostat operation, you can reset the thermostat by removing the wires from terminals R and C (do not short them together) and removing batteries for 2 minutes.