INSTRUCTION MANUAL FIRST MADE FOR SA-97P,SA-127P & SA-187P MATERIAL OR MODEL *PAPER-JO DIMENSION OR MAKER WOODFREE 80gm COLOR BLACK Print APPROVALS N.Yamazaki 2007/Nov/28 CHECK Tai C. S 2007/Nov/21 DESIGN Tai C. S 1. Change Text of Cover, Pg 2, 7 2007/Nov/21 Tai C.S...
Thank you for choosing SANYO air conditioner. Our design is based on the best efficiency and the lowest noise operation and it can keep the room comfortable. Please read this Instruction Manual carefully before operating the unit and keep it for consultation. If you still have any difficulties or problems, consult your dealer for help.
Function and working temperature range Introduction Window type room air conditioners of SANYO can regulate the room temperature,dry the room. It is convenient for your work,study and life. It can be widely used in residence, shop, hotel, office, library and laboratory, and so on.
Operating condition Please operate air conditioner in correct conditions as following: Cool mode operation 1. Outdoor temperature should be in range of 19 to 43 . Otherwise it is possible for air conditioner to breakdown. 2. Room temperature should be in the range of 19 to 32 .
Installation Installation precaution: Window type conditioner is so valuable and the improper installation of it will cause a lot of damage! Please associate the professional techni- cian to install the unit and don’ t install it by yourself. Otherwise, we are not responsible for the damage like this. Before installation, check that the voltage of the electric supply in your home or office is the same as the voltage shown on the name plate.
Installation procedure: Horizontal line 1) Remove the sticker from the front panel. 2) Put the unit into the installation hole. When installing the unit, it should be slanted down to the back to avoid the enlargement of noise or vibration. (Slant between 6-10mm.) (Shown at right figure.) The installation place should be strong enough to avoid the enlargement of noise or vibration.
Exterior View Inside View Screw Bottom Side View Exterior V iew Inside V iew of Drainage Pan Drainage Pan Remove the rubber plug Screw Bottom Side V iew Drainage Pan of Drainage Pan Note: Drain hose or tubing can be purchased locally to satisfy your particular needs. The drainage pipe shall be steadily connected with the drainage faucet without leakage.
Part identification Control panel Air direction adjustment Vertical airflow direction vane (Airflow direction adjustment up and down). The vertical airflow direction vane is controlled by positioning the vane to discharge the air upwards, downwards or straight out.
Air conditioner operation Press this pad for turning the air conditioner ON and OFF. ON / OFF This area will show the set temperature (from 16 C to 30 C) and, if in the TIMER DISPLAY mode, it will show the ON and OFF settings of the TIMER (from 1 to 24 HR). Press this control pad to select the operation of “FAN”...
Operation tips Operation for comfort and economy Do not overcool the room Adjust the vertical and Keep blind or curtains closed, temperature, this is not good for horizontal airflow direction to Do not let sunshine enter the room directly when the air health and waste electricity.
Caution 1) T he plug must be accessible after the appliance is positioned. 2) Do not use this appliance in the laundry. 3) If the power cord is damaged, it must be replaced by the manufacture or its service agent in void of hazard. Do not use the air conditioner Do not pull out the power cord.
Care and maintenance Always turn off the air conditioner and main power supply before cleaning to ensure safety. Clean unit Air filter 1. Plug out first before cleaning. The air filter behind the intake grille should be washed at least every two weeks or as often as it needs cleaning.
When trouble shooting If your air conditioner does not work properly, first check th e following items before for servicing, it help to save your time and money. If it still does not work properly, then only contact your dealer or service center. Fault phenomenon Trouble-shooting * Is power fail?
Immediately stop all operations and plug out, contact with your dealer in the following situations. * Electrical lines are much hot or lines cover * Operation starts or stops abnormally; breaks; * Power fuse or switch often breaks; * Other strange situations. * Carelessly splash water or something into air conditioner;...
Branch Product Warranty Certificate This quality SANYO product is guaranteed for one (1) year from the date of purchase of original buyer against defect in manufacture or material. The compressor is guaranteed for five (5) years while refrigerant and other consumable items are not covered by this warranty after one (1) year from the date of original purchase.