• This smoke alarm may be interconnected with as many as 11 other Firex model FADC, AD and ADC smoke alarms, or as many as 6 Firex model ADH heat alarms for a total of not more than 18 interconnected devices.
MAY be used inside individual rooms as SUPPLEMENTAL protection. • Install a smoke alarm in every room and on every level of the home. Smoke may not reach the smoke alarm for many reasons. For example, if a fire starts in a remote part of the home, on another...
THIS SMOKE ALARM SHOULD BE INSTALLED IN ACCOR- DANCE WITH THE NATIONAL FIRE PROTECTION ASSOCIA- TION’S STANDARD 72 (National Fire Protection Association, Batterymarch Park, Quincy, MA 02269). Install smoke alarm on a 4-inch octagon or single gang • junction box only. 1. From back of smoke alarm, remove mounting plate.
• This smoke alarm may be interconnected with as many as 11 other Firex model FADC, AD and ADC smoke alarms, or as many as 6 Firex model ADH heat alarms for a total of not more than 18 interconnected devices. DO NOT connect to any other type or model smoke alarm.
Alarm Control then resounds the alarm, the smoke is too heavy and could be a possibly dangerous situation— take emergency action. TESTING THE SMOKE ALARM • Test each smoke alarm to be sure it is installed correctly and operating properly. • Test all smoke alarms in an interconnected system after installa- tion.
• Using the soft brush or wand attachment to a vacuum cleaner, vacuum all sides and cover of smoke alarm. Be sure all the vents are free of debris. • If necessary, turn off power and use a damp cloth to clean smoke alarm cover.
Ultralife U9VL-J 9-volt battery (when sold with Invensys Controls Americas smoke alarm) provided that it is returned with postage prepaid and with proof of pur- chase date to Invensys Controls Americas. This warranty does not cover damage resulting from accident, misuse or abuse or lack of reasonable care of the product.