Lossnay Models: LGH-15RX LGH-25RX LGH-35RX LGH-50RX LGH-65RX LGH-80RX LGH-100RX LGH-150RX LGH-200RX Operating Instructions (For the user) Please read through these instructions in order to familiarize yourself with the proper and safe procedures for operat- ing the Lossnay. After reading this manual, keep it in an easily accessible and safe place for future reference. Safety precautions The following signs indicate that death or serious injury may be caused by a failure to heed the precautions described below and the resultant mishandling of the product.
Models LGH-15 to 100 RX Models LGH-150 and 200 RX Damper Damper This is to be incorporated and used in the Mitsubishi Electric Air- Conditioner Network System. Exhaust air This is interlocked with the City Multi and operated by it.
Operation (Continued) 1. Reduces cooling load 3. Office equipment room cooling If the air outside is cooler than the air inside the building during During cold season, outdoor air can be drawn in and used as is the cooling season (such as early morning or at night), “By-pass” to cool rooms where the temperature has risen due to the use of ventilation will draw in the cooler outside air and reduce the cool- office equipment.
Maintenance (Continued) Assembly after maintenance 2. Press the filter button on the remote controller (PZ-41SLB-E) two times in succession. (This clears the Lossnay’s operating time cumulative data.) 1. Bearing in mind the following points, assemble the parts following the sequence for their removal in reverse. Relevant button Relevant display items •...