A Heat or Cool indicator is located on the bottom middle cover of the thermostat. See Fig. 2. The light will be red if the thermostat is in Heating mode. The light will be green if the thermostat is in Cooling mode.
Use the UP ARROW and DOWN ARROW buttons to set the maximum number of Occupied periods avail- able. The thermostat can be set to 1, 2, or 3. After the number of Occupied periods has been selected, press the Mode button.
Mode and UP ARROW buttons at the same time to exit Programming mode. NOTE: The thermostat will continue to follow the schedule until a new one is entered. • If only one occupied schedule is selected, the Occupied 2 and 3 schedules are skipped.
OPERATION The Mode button selects the operating mode of the ther- mostat. If OFF is selected, the thermostat will not enter Heat- ing or Cooling mode. If HEAT is selected, the thermostat will only enter Heating mode (if the room temperature is below the heating set point).
Copyright 1999 Carrier Corporation Manufacturer reserves the right to discontinue, or change at any time, speciﬁcations or designs without notice and without incurring obligations. Book 1 PC 111 Catalog No. 533-347 Printed in U.S.A. Form 33CS-11SO Pg 8 2-99 Replaces: New...