LEN (Local Equipment Network) com- munications bus only. Do NOT connect the Navigator module to the CCN (Carrier Comfort Network®) con- nector, as it may damage the device. 3. See Fig. 2-8 for Navigator LEN connection locations in the units.
LEN port. On power up, the Navigator module displays: ComfortLink Navigator Carrier The Navigator module will upload the appropriate display tables from the Main Base Board (MBB) that it is connected to. A ‘Communication failure’ message will be displayed if any errors are encountered.
If an area is entered that is Password Protection — password protected or an item is selected for change that is password protected, the Navigator™ module will display: Enter Password The first digit of the password will be flashing. Hold either of the arrow keys down to change the value of the first digit (if necessary) and press to accept.
5. Insert the rubber grommet (included with new cable as- sembly) into the cable entrance hole. Copyright 2006 Carrier Corporation Manufacturer reserves the right to discontinue, or change at any time, specifications or designs without notice and without incurring obligations.