Single and Double Element Models, Residential 20–120 Gallon Model: HE Series, GE Series, PE Series, SE Series The purpose of this manual is twofold: one, for the contractor, to provide the installer with basic directions and recommendations for the proper installation and adjustment of the water heater;...
READ THIS MANUAL Inside you will find many helpful hints on how to use and maintain your water heater properly. Just a little preventive care on your part can save you a great deal of time and money over the life of your water heater.
Water temperatures above 125°F can cause severe burns or death from scalding. Be sure to read and follow the warnings outlined on the label pictured below. This label is also located on the water heater near the thermostat access panel.
Be sure to read and understand the entire Use and Care Manual before attempting to install or operate this water heater. It may save you time and cost. Pay particular attention to the Safety Instructions. Failure to follow these warnings could result in serious bodily injury or death.
Inspect Shipment Inspect the water heater for possible damage. Check the markings on the rating plate of the water heater to be certain the power supply corresponds to the water heater requirements. heater plus 2″ min.
The suggested method of controlling thermal expansion is to install an expansion tank in the cold water line between the water heater and the check valve (refer to the illustration below). The expansion tank is designed with an air cushion built in that compresses as the system pressure increases, thereby relieving the over pressure condition and eliminating the repeated operation of the relief valve.
Automatic Gas Shut-Off Devices for Hot Water Supply Systems, ANSI Z21.22, is supplied and must remain installed in the opening provided and marked for the purpose on the water heater. No valve of any type should be installed between the relief valve and the tank. Local codes shall govern the installation of relief valves.
The water heater is completely wired to the junction box inside jacket at the top Water heater junction box. front of the water heater. An opening for 1/2″ or 3/4″ electrical fitting is provided CAUTION: The presence for field wiring connections.
Installing the water heater. Relief Valve Insulation Installation CAUTION: Ensure the T&P Valve opening is not obstructed by the insulation. Typical top connection arrangement For increased energy efficiency, some water heaters have been supplied with a 2-3/8” section of pipe insulation.
Area free of flammable vapors. Sufficient fresh air supply for proper operation of water heater. Water Supply Water heater completely filled with water. Air purged from water heater and piping. Water connections tight and free of leaks. Relief Valve Temperature and Pressure Relief Valve properly installed and discharge line run to open drain.
Operating the water heater. CAUTION: Hydrogen gas can be produced in a hot water system served by this water heater that has not been used for a long period of time (generally two weeks or more). HYDROGEN GAS IS EXTREMELY FLAMMABLE!! To dissipate such gas and to reduce risk of injury, it is recommended that the hot water faucet be opened for several minutes at the kitchen sink before using any electrical appliance connected to the hot water system.
This is normal for heat trap fittings when in operation and does not indicate a need for service. Wait for the water heater to recover after an abnormal demand. Replace fuse or reset circuit breaker. Make sure electric supply to water heater and disconnect switch, if used, are in the ON position.
Heating element Heating element Drain valve shroud **Not supplied on all models The model and serial number of the water heater from the rating plate. Specify voltage and wattage as marked on the rating plate. **Heat Trap **Nipple Dip tube gasket...
Replace the insulation and jacket access panel(s) before turning on the power to the water heater. N N O O T T I I C C E E : : T T h h e e c c a a v v i i t t y y i i n n s s e e r r t t c c r r o o s s s s b b a a r r i i s s n n e e c c e e s s s s a a r r y y f f o o r r t t h h e e m m a a n n u u f f a a c c t t u u r r i i n n g g p p r r o o c c e e s s s s o o n n l l y y .
Wiring diagrams. Wiring Diagrams for Type–59T Therm-o-disc Thermostats Single Element Models Double Element Models BRANCH CIRCUIT TO ELECTRICAL DISTRIBUTION PANEL 240 V. THERMOSTAT & HIGH TEMP. LIMIT (ECO) HEATING ELEMENT YELLOW BLACK LOWER HEATING ELEMENT BRANCH CIRCUIT TO ELECTRICAL DISTRIBUTION PANEL 240 V.
Follow these three steps to protect your new appliance investment: Complete and mail this Consumer Product Ownership Registration today. Model Number If you require service, call 800-431-1549. Consumer Product Ownership Registration Water Heater Mrs. Miss First Name Last Name Street Address Apt.